This consultation closes at 11:59 p.m. on:
February 22, 2023
MCDOUGALL ENERGY INC. wants to replace several tank and dispenser sump entry boots (fittings that connect piping to a containment system) with retrofit boots made by Icon Products.
645 ARTHUR ST W
THUNDER BAY, ON
Site location details
MCDOUGALL ENERGY INC.
421 BAY ST, SUITE 301
SAULT STE MARIE, ON
1.3.1. Equipment installed at a facility or on a highway tank shall be approved and installed in accordance with the requirements of this Code and the manufacturer’s instructions, and shall be appropriate for the service for which it is intended.
Why the Code Would Not be Met
Clause 1.3.1 of the Liquid Fuels Handling code requires that equipment be approved to a Canadian standard; however, there is no corresponding Underwriters’ Laboratories of Canada standard.
These retrofit boots will allow the applicant to make repairs to the dispenser sumps without having to excavate and replace the entire sump.
The retrofit boots have been evaluated by a third-party lab and meet the Underwriters’ Laboratory standard "UL 2447 Outline of Investigation for Containment Sumps, Fittings and Accessories for Fuels". The retrofit boots have also shown good cold weather performance.
TSSA assesses that there is likely to be no environmental impact should this variance be granted.
View materials in person
Some supporting materials may not be available online. If this is the case, you can request to view the materials in person.
Get in touch with the office listed below to find out if materials are available.
Connect with us
Sign up for notifications
We will send you email notifications with any updates related to this consultation. You can change your notification preferences anytime by visiting settings in your profile page.Follow this notice